Superheater desuperheating water temperature monitoring
Reheater desuperheating water temperature monitoring
Temperature monitoring of outlet header of suspension pipe
Temperature monitoring of feed water main
The main water supply pipe of the boiler generally adopts welded integral drilling temperature casing pipe or high-temperature and high-pressure temperature casing pipe. The material of the temperature casing pipe can be WB36, and the temperature range is between 0~600℃. Recommended model is TCK-S0213/WB36-38-UL.
Boiler desuperheating water measuring points include: superheater desuperheating water and reheater desuperheating water. Generally, high-temperature and high-pressure thermocouples are used. The temperature range is between 0~600℃. The diameter of the sheathed jacket of the sheathed element is Φ3, Φ4, Φ5 and Φ6 for options. Generally, Φ5 or Φ6 is most commonly used. Double-piece elements are recommended. Recommended product model is TCK-S0213/316-38-UL.